Having your boiler serviced once a year by a Gas Safe registered engineer ensure that you
maintain your guarantee after the first year.
avoid future repairs when problems are spotted early.
save energy as our engineer will check your boiler is running efficiently.
increase its life expectancy.
Most importantly an annual service ensures that your boiler is safe.
Make sure you arrange for regular servicing as carbon monoxide leaks may be fatal.
To maximise performance and reliability, it's important to keep your boiler and heating system well maintained
FREE help and advice for customers, Paperless system, NO handwritten bits of paper, PDF documentation via your email, Service records, service reminders, appliance records, service and repair history, Gas Safety Certificates issued, PDF to your email on site, Email confirmation. Payment via web site, or BACS,
The Landlord Gas Safety Record, Gas Safety Certificate, CP12 Form,
A gas safety check is different from a gas service. It is primarily designed to inspect any gas appliances including boilers, cookers and fires (permanent or portable)to ensure they are working correctly and safely. A gas safety check MUST be carried out by a Gas Safe Registered engineer.
A gas safety certificate is a document that confirms that appliances have been tested for safety as part of a gas safety inspection. Here in the UK, it is the law that all landlords and owners of commercial property have their gas appliances inspected annually to ensure they are safe and working properly all flues and pipework within the property, as well as any gas appliances that were supplied to the tenants.
As a homeowner, you should arrange for this check to be carried out every 12 months. Andy explains that 'landlords have a duty of care to their tenants' to make their properties gas safe by obtaining a Gas safety certificate (CP12) every 12 months.
All engineers are fully qualified, Gas Safe Registered and very experienced plumbers. Over the years we have been providing plumbing and heating services for residents and local businesses in all areas of London. With all the qualifications and years of on the job plumbing experience, our plumbers and heating engineers can fix almost every type of plumbing, heating or boiler related problem. For our plumbers no job is too big or too small and every job gets treated with the same importance. Whether it is a general routine boiler check-up you require or a full blown burst pipe, we can help and we will be with you in no time. Our policy has always been to turn up when we say we will, only do jobs that need doing, do the jobs properly and to the highest standards. For more information or to request a plumbing job visit our website or give us a call.
1 hour require for this cp6
Maintenance work Interval
1 Ask the end user whether any significant problems occur when operating the product Annually
2 Use the diagnostics system to check the product's fault history Annually
3 Visually inspect whether the air/flue pipe and its opening have been installed correctly in accordance with the set-up instructions Annually
4 Check that the unit has been installed correctly and the connections have been secured Annually
5 Check all of the connections for tightness Annually
6 Check that the condensate pipe is in good condition, that it is leak-tight and that the drain is correct Annually
7 Check whether all of the externally routed condensate pipes are dimensioned correctly and have been insulated sufficiently (frost protection) Annually
8 Check whether the gas flow rate corresponds with the specifications on the data plate and lies within the tolerances specified in these instructions Annually
9 If the gas flow rate lies outside of the tolerances specified in these instructions, eliminate the fault in accordance with the regulations and the current technology Annually
10 Check the general condition of the product and, if required, eliminate any faults that are found Annually
11 Carry out the combustion analysis: Measure the CO content, CO₂ content and the CO/CO₂ ratio. For products with a rear air/flue connection: The combustion analysis can only be carried out when the unit casing has been removed; it is not necessary to test these products for flue gas recirculation Annually
12 Check the product's recirculation at the supply air test point on the air/flue pipe. If required, inspect the entire air/flue system and, if necessary, correct the fault Annually
13 Disconnect the product from the electrical installation Annually
14 Check and, if required, correct the electrical installation Annually
15 Remove the unit casing, check the condition of all of the functional components, in particular for leaks, corrosion, rust, etc. and, if required, repair any damage Annually
16 Visual inspection of the heat exchanger and burner seals Annually
17 Carefully clean the inside of the product: The air passages to the burner must be clear and clean Annually
18 Close the installation's gas stopcock and, if required, service valves Annually
19 Check the quality of the heating water: Clarity (clouding), correct inhibitor and pH value Annually
2 hours require for this cp6
20 Removing the gas-air mixture unit If required, at least every 5 years 23
21 Checking the burner If required, at least every 5 years 24
22 Cleaning the condensate trap Annually 25
23 Filling the condensate trap Annually 18
24 Cleaning the heat exchanger If required, at least every 5 years
24 Appendix 0020238195_05 ecoTEC plus Installation and maintenance instructions 27
25 Check and, if required, replace the insulating mat in the burner area If required, at least every
5 years 26 Installing the gas-air mixture unit If required, at least every 5 years 25
27 Reassemble the product After each time maintenance work is carried out
28 Open the service valves, carry out the required leak-tightness test Annually
29 Fill the product/heating installation to the filling pressure specified for the system Annually
30 Connect the product to the electrical installation Annually
31 Run the test operation on the product/heating installation including hot water generation (if available) and, if required, purge the product/heating installation Annually
32 Record all of the analysis results in the Benchmark service record in these instructions Annually